The APC by Schneider Electric Rack Power Distribution Unit (PDU) may be used as a stand-alone, network- manageable power distribution device or up to four devices can be connected together using one network connection. The Rack PDU provides real-time remote monitoring of connected loads.
The HSYCO RACKPDU driver supports the AP88XX and AP78XXB Metered models.
In order to be able to control the device with HSYCO SERVER, remote access to the command line interface via SSH must be enabled.
Add a RACKPDU I/O Server in the I/O Servers section of the Settings and set its parameters:
- IP Address: the IP address of the device
- IP Port: TCP/IP port to use (defaults to 22)
- User: the SSH user (defaults to "apc")
- Password: the SSH password (defaults to "apc").
- Shutdown when inactive: defaults to false.
|startupevents||false||true||generate IO events also during the driver’s start-up phase|
|false||start generating events only after HSYCO is aligned with the current status of the system|
All measured values returned as datapoints use the units as set in the PDU. The unit is not returned in the datapoint value.
|offline||R||not connected to the PDU|
|bklowload.<N>||<value>||R||bank N low-load threshold current in amps|
|bknearover.<N>||<value>||R||bank N near-overload threshold current in amps|
|bkoverload.<N>||<value>||R||bank N overload threshold current in amps|
|devlowload||<value>||R||low-load threshold in kilowatts for the device|
|devnearover||<value>||R||near-overload threshold in kilowatts for the device|
|devoverload||<value>||R||overload threshold in kilowatts for the device|
|humreading||<value>||R||humidity value from the sensor (%RH)|
|phlowload.<N>||<value>||R||phase N low-load threshold (amps)|
|phnearover.<N>||<value>||R||phase N near-overload threshold (amps)|
|phoverload.<N>||<value>||R||phase N overload threshold (amps)|
|tempReading||<value>||R||temperature value in Celsius|
|bkpeakcurr.<N>||<value>||R||bank N peak current measurement in amps|
|bkreading.<N>||<value>||R||bank N current reading (measurement) in amps|
|devpeakload||<value>||R||peak power measurement in kilowatts from the device|
|devreading.power||<value>||R||total power in kilowatts for the device|
|devreading.energy||<value>||R||total energy in kilowatt-hours for the device|
|devreading.appower||<value>||R||total apparent power in kilovolt amperes for the device|
|devreading.pf||<value>||R||total power factor for the device|
|phpeakcurr.<N>||<value>||R||peak current measurement from phase N (amps)|
|phreading.current.<N>||<value>||R||measured current for phase N (amps)|
|phreading.voltage.<N>||<value>||R||measured voltage for phase N (volts)|
|phreading.power.<N>||<value>||R||measured power for phase N (watts)|
|phreading.appower.<N>||<value>||R||measured apparent power for phase N(va)|
|phreading.pf.<N>||<value>||R||measured power factor for phase N|
|hp||<value>||R||hail peak intensity (hits/cm2h, hits/in2h, hits/ h)|
|th||<value>||R||heating temperature (C, F)|
- initial version release
APC, StruxureWare, and PowerNet are trademarks owned by Schneider Electric Industries, S.A.S., or its affiliated companies. All other trademarks are property of their respective owners.